Float Level Switches & Sensors with Magnetic Reed Switches for Continuous Level Measurement.
Float level sensor (float switch) is one type continuous level sensor for industrial level measurement. Float level sensor has a magnetic float that rises and falls as liquid level changes. The movement of the float creates a magnetic field. Through the magnetic coupling effect, the internal resistance of the sensor changes linearly. The resistance change is converted into a standard current signal of 4 ~ 20mA by an intelligent converter. The percentage of the liquid level, 4 ~ 20mA current and liquid level value, can be displayed on site. Applications like: water tank, fuel tank, level measurement and level control. Vertical, horizontal, and side mounted, all can be satisfied.
Description of SI-U01 Float Level Sensor
SI-U01 float level meter is composed of three parts: magnetic float, sensor and transmitter. When the magnetic float changes with the liquid level, it floats up and down along the duct. The magnetic steel inside the float attracts the reed switch at the corresponding position in the sensor. So that the total resistance (or voltage) of the sensor changes. The changed resistance (or voltage) signal is converted into a current signal of 4-20mA and output. And the upper and lower limit alarms can be set on the display to achieve the position control of the liquid level.
SI-U01 floating ball liquid level gauge consists of a liquid level sensor and an intelligent HART board (current converter). The floating ball and the liquid level change synchronously, and the reed switch is controlled to open and close. This makes the resistance in the sensor change linearly. The change of resistance is converted by the converter into 4 ~ 20mA standard current signal or superimposed HART digital signal output.
Features of SI-U01 Continuous Float Level Sensor
- Intelligent electronic components are composed of a motherboard and an LCD screen;
- You can adjust the range and zero point by pressing the button on the spot;
- It can use HART communicator or microcomputer to communicate with this smart meter on both sides without interrupting the output signal. It is suitable for explosion-proof or inconvenient installation and disassembly of the meter. Instrument measurement, process parameters, equipment configuration, calibration, diagnostic information HART protocol access or change;
- Two-way communication with the host in the distributed control system using the HART protocol;
- With EEPROM, no data is lost due to power failure.
- Simple working principle, wide applicability, safe, convenient and maintenance-free
- Realize the connection measurement of the liquid level without being affected by the physical and chemical properties of the measured medium. Such as: temperature, pressure, conductivity, dielectric constant, etc.
- The use of different materials can achieve the measurement of highly corrosive media
- It can be used to measure the interface of two different density liquids.
- Good repeatability.
Specifications of SI-U01 Float Level Sensor
|Max insert depth||L=6m(>6m customize)|
|Max control scope||L-120mm|
|Min control scope||50mm(<50mm customize)|
|Working pressure||PN2.5~ PN160(Max pressure PN320)|
|Working temperature||-40~80 °C, -40~120 °C, -40~150 °C (250°C customize )|
|Float diameter||D28~D120(depending on pressure and density)|
|Installation type||Flange: DN40~DN150|
Flange standard: HG/T20592~2009
Other method (consulting)
|Maximum switch frequency||<1×105|
|Working power supply||220VAC/380VAC|
|Max voltage of switch||<250VAC|
|Max current of switch||5A|
|Installation angle||< ±25°|
|Wiring box||M20×1.5 female thread|
|Explosion-proof grade||Exd II CT6Gb|
Float Level Sensor Operating Principle
Float level meter is an instrument for measuring liquid level. It is widely used in the field of liquid measurement. Many industries will choose to use it for measurement equipment. Such as the petroleum, chemical, and pharmaceutical industries.
Float level sensor: Float level sensor is designed and produced based on the principle of buoyancy and static magnetic field. The position of a floating ball with a magnet (floating ball for short) in the measured medium is affected by buoyancy. The change of the liquid level causes the position of the magnetic float to change. The role of the magnet and sensor (reed switch) in the floating ball changes the number of components (such as fixed resistance) connected in series to the circuit. Thereby changing the electrical quantity of the instrument circuit system. That is, changes in the position of the magnetic float cause changes in the electrical quantity. The change of the electrical quantity is detected to reflect the liquid level in the container.
The float level sensor is installed on the top of the container through a connection flange. The float ball floats on the liquid surface according to the principle of discharging the liquid volume phase and so on. When the liquid level of the container changes, the float ball also moves up and down. The reed switch of the ball level gauge is magnetically attracted to change the position of the liquid level into an electrical signal. The actual position of the liquid is displayed digitally by the display instrument. The floating ball level gauge can achieve long-range detection and control of the liquid level.
Applications of SI-U01 Float Level Sensor
Float level sensors provide reliable readings in a range of operating environments.
Float level sensor can be widely used for continuous measurement of the liquid level (boundary level): High temperature. High pressure. Viscous, dirty media. Asphalt, wax-containing oil products and flammable, explosive, corrosive media.
Float level sensor can be used for industrial level measurement and control of various liquid tanks. Such as: Petroleum, chemical raw material storage. Industrial processes, biochemicals, medicine, food and beverage. Tank farm management and underground storage at gas stations.
The float level sensor is also suitable for dam water level, reservoir water level monitoring and sewage treatment, etc.
Of course, for different applications, you can choose different materials.
Plastic materials PP and PVDF, suitable for strong acid and alkali places;
The metal material is SUS304 / 316L, which is suitable for high temperature 200 ℃ and high pressure 64kg / cm2.
Float level sensor Advantages and Disadvantages
- Long life span, stable and reliable operation, easy installation, almost no maintenance
- None influence of measured medium in physical and chemical state. Eg: medium electrical conductivity, dielectric constants, foam, pressure, temperature, evaporation, boiling, bubbling effect etc, .
- Choose appropriate material can be used in a variety of bad media environment with densities ≥ 0.5G/CC ;
- Interface measurement with two media of different density control;
- Wide range of application. Pressures from vacuum to PN160 (special up to PN320), temperature -40~+150 ° c
- Design, explosion-proof, suitable for explosive environments;
- Controller can be used to control the upper and lower liquid level.
- Low accuracy.
- The installation position is limited by the shape of the container.
- Most float level gauges are not suitable for corrosive or hazardous liquid media.
SI-U01 Float Leve Sensor Installation
The main float level sensor installation methods are:
Top mounted; Bottom mounted; Side mounted
SI-U01 Float level sensor installation instructions:
- The measured medium should not contain ferromagnetic impurities.
- In order to prevent the floating ball from falling off or hitting the sealing tube at high speed during transportation, which will cause the measuring tape to come out. The meter should be fixed to the bottom of the sealed tube with a clamp and the magnetic steel on top of the sealed tube before the instrument leaves the factory. Before installing and using, the user should remove the clamp. Raise the floating ball to the top of the sealing tube. And then slowly move the floating ball down, and the needle should be rotated accordingly.
- The indicator of the meter is pointer type, the indicator numbers are arranged in the direction of gel needles during full-scale measurement, and the indicators are arranged in the counter-clockwise direction during emptyness measurement.
- The instrument is equipped with a mounting flange when it leaves the factory. The user should have a pipeline flange.
- The installation position of the instrument is generally selected at half of the measuring range.
Float level sensor price
The float level sensor is a fully customized product. Different measurement needs will cause price changes. So before determining the price of the float level sensor, we need to confirm:
1.Junction box style
- Connection method
- Probe diameter
- Float distance
- Probe length
- Material selection
Sino-Instrument is float level sensor manufacturer. On the premise of ensuring product quality, we offer you the best price.
Many people may confuse the float level sensor with the magnetostrictive level sensor. Because they look alike. But the actual working principle is different.
Tank level senor is a level sensor used to measure the tank level. The liquid level is the level of the liquid in a sealed container (such as a water tank) or an open container (water tank). The instrument that measures the liquid level is called a liquid level sensor, a liquid level gauge or a liquid level transmitter. The liquid level sensor is a kind of level instrument. Hydrostatic, Ultrasonic, Magnetostrictive, Radar, Differential Pressure are commonly choices for tank level measurement. Liquid level sensors have been around for decades for leak detection or level measurement. Common measured medium are: Water, Fuel, Diesel, Gasoline, diesel, liquefied gas, liquid ammonia, etc.
Diesel Fuel flow meters are digital flow meters for liquid fuel consumption measurement.
Most widely used types are mechanical and digital inline fuel meters. Differential flow sensors are avilable. Like: the turbine, positive displacement (oval gear), Coriolis, and differential pressure flow meters. Sino-Instrument offers a variety of fuel flow meters for most fuels. Including diesel, bio-diesel, kerosene, gasonline, oil, heating oil, grease and certain chemicals.Sino-Instrument offers diesel fuel flow measurement solutions and free technical support. If you have any question for diesel fuel flow measurement, please contact us.
Float level sensor uses magnetic float as the measuring element. Through magnetic coupling, the internal resistance of the sensor changes linearly. The smart converter converts the resistance change into a 4-20mA standard current signal. It can display the percentage of liquid level, the current of 4 ~ 20mA and the value of liquid level. Remote transmission control room can realize automatic detection, control and recording of liquid level. This instrument is suitable for petroleum, chemical, power, light industry and pharmaceutical industries, such as sewage treatment and medium level measurement in various atmospheric and pressure vessels, especially for underground tanks and tanks.
Float level gauge is composed of float, plunger and so on. The float ball level gauge is mounted on the top of the container through a connecting flange. The float floats on the liquid surface according to the principle of discharging the liquid volume phase and so on. When the liquid level of the container changes, the float also moves up and down. Due to the magnetic effect, the reed of the float level gauge is magnetically attracted and changes the liquid level position into an electrical signal. The actual position of the liquid is displayed digitally by the display instrument. The float level gauge thus achieves long-range detection and control of the liquid surface.
Liquid level switch, also known as water level switch, liquid level sensor. As the name suggests, it is a switch used to control the liquid level. It is mainly divided into contact type and non-contact type. Capacitive liquid level switches are commonly used in non-contact switches, and contact float type liquid level switches are most widely used. Electrode level switches, electronic level switches, and capacitive level switches can also be implemented using contact methods.
1. Float level switch: The magnetic float of the float level switch rises or falls with the liquid level. So that the sensor detects the position of the reed switch chip in the tube, and sends a contact on / off switch signal. Because of its simple structure and economic benefits, it is widely used in the market, mainly for civilian use. But its stability is relatively poor compared to industrial-grade products.
2. Capacitive liquid level switch: After the probe is wetted, it detects the change in capacitance value and outputs a contact signal. Which has certain advantages in the measurement of slightly viscous media.
3. Electrode type liquid level switch: The electrode type liquid level switch uses the conductivity of the liquid to detect the level of the liquid. Once the measured medium touches the pole, it will conduct electricity and detect the signal. After the signal of the controller is amplified, a contact signal is output to realize the control of the liquid level.
4. The photoelectric liquid level switch: The photoelectric liquid level switch uses infrared detection, using the principle of refraction and reflection of light. The reflection or refraction of light at the interface between two different media. When the measured liquid is at a high level, the measured liquid and the photoelectric switch form an interface. When the measured liquid is at a low level, air and the photoelectric switch form another interface. These two interfaces make the photoelectric switch internal light. The intensity of the reflected light received by the receiving crystal is different, that is, it corresponds to two different switching states. Generally speaking, compared with other measuring instruments, the applicability of photoelectric switches is poor.
5. Tuning Fork Liquid Level Switch: It outputs a switch signal by detecting the change in the frequency and amplitude of the fork’s vibration, which is highly versatile. For the viscous working conditions, please consult with the manufacturer to determine the working conditions that are easy to crystallize.
6. Ultrasonic external liquid level switch: The instrument probe emits ultrasonic waves and detects its residual vibration signal in the container wall. When the liquid passes through the probe, the amplitude of this residual vibration signal will become smaller. This change is detected by the instrument After that, a switching signal is output. It is a non-contact type and is often used in high-risk situations where it is difficult to open holes on the site, but the cost is relatively expensive.
The above is an introduction to the types of common level switches in the market. For more information about level switches (level switch, level switch), level meters (level meter, level meter) and other level measuring instruments, please contact us.
Float switch is a kind of special switch. Because it does not need power supply to provide power, it is a very simple pressure switch. Its volume is small, the material is stainless steel or plastic, and the working life is very long. It has been widely used in water treatment.
The advantage of the float switch is that it can accurately measure the water level of the liquid. So it is generally used in the liquid detection of normal pressure or pressured storage tanks for signal transmission, such as liquid level alarm. Strong. It can accept multi-point control, and its use position can be left to the customer. It does not need a power supply to ensure its environmental protection. Its life is about 2 million switches. No matter the price of the product itself or the installation cost are very affordable, the price is very high. High degree of protection. It can work under high temperature or high pressure conditions, and has high safety.
Sino-Instrument offers over 10 level transmitters for level measurement.
About 50% of these are liquid level meters,
40% is the tank level sensor.
A wide variety of level meters options are available to you,
such as free samples, paid samples.
Sino-Instrument is a globally recognized supplier and manufacturer of level measurement instrumentation, located in China.
Request a Quote
Continuous Float Level Sensor & Switches-Sino-Instrument
Float level sensor (float switch) is one type continuous level sensor for industrial level measurement. Float level sensor has a magnetic float that rises and
Product SKU: SIU-FLO
Product Brand: Sino-Inst
Product Currency: USD
Product Price: 260
Price Valid Until: 2028-06-08T21:55:16
Product In-Stock: https://schema.org/InStock